National Fire Protection Association 1 - Outdoor Storage Locker
NFPA 1: Fire Code 66.14 Hazardous Materials Storage Lockers
66.14.1* Scope. This section shall apply to the storage of liquids in movable, modular prefabricated storage lockers, also known as hazardous materials storage lockers (hereinafter referred to as lockers), specifically designed and manufactured for storage of hazardous materials, in the following:
(1) Containers that do not exceed 119 gal (450 L) individual capacity
(2) Portable tanks that do not exceed 660 gal (2500 L) individual capacity
(3) Intermediate bulk containers that do not exceed 793 gal (3000 L) individual capacity
66.14.3 General Requirements.
188.8.131.52 Lockers that ar……..
NFPA 1: 66.14.5 Designated Sites for Hazardous Materials Storage Lockers
184.108.40.206 Lockers shall be located on a designated approved site on the property. [30:14.5.1]
220.127.116.11 The designated site shall be arranged to provide the minimum separation distances specified in Table 18.104.22.168 between individual lockers, from locker to property line that is or can be built upon, and from locker to nearest side of public ways or to important buildings on the same property. [30:14.5.2]
Table 22.214.171.124 Designated Sites (See Table)
Please consult your local authority having jurisdiction with your questions and for guidance in conforming to laws as they apply to your application. This is only meant for a reference and does not imply a warranty.